We thank you for choosing 16JH type single effect hot water -heated Absorption. The operators are asked to fully understand the instructions in this manual. The following are the general safety instructions for operators. More detailed instructions. For lifting or moving a water box cover or other. Use such an aid even for lifting or moving light machine ry if the.
|Published (Last):||1 August 2015|
|PDF File Size:||17.18 Mb|
|ePub File Size:||11.59 Mb|
|Price:||Free* [*Free Regsitration Required]|
Energysaving with minimizedstartup. Startup time of the system has been cr,it short with an optimized flow rate of circulating solution responsive to the startup operationquickly. This reduce fuel consumption. Operatingconditionis displayedon the panel digitally. Temperature in the high temperature generator. Dew point temp. Inlet or Outlet temperature in the cooling water. Chiller-Heater operating time. Operating time of the refrigerant pump.
Temperature of the exhaust gas. Temperature of the evaporating refrigerant. Fuel control valve indicator.
Combustion time Operating time of the solution pump. Preventionfunction for unusual shut down on failure are equipped. With confinuous monitoringoperating conditions by sensors equipped in the unit, stoppage of the system on failures or fault is minimized in controlling system before the system goes to failures.
Dew-point control of the high temperature generator. Solution temperature control of the high temperature generator. Pre-alarm system ensure preventive maintenance. Rising in the internal pressure. Replacement timing of the burner part. Fault in thermo-sensors. The x mark indicates that only counting.
Rising in LTD of cooling water. Overload in the purge pump. Replacement timing for respective oarts. Abnormal in level control in high temPerature generator.
Reducingdilution time at the time of operating interruption. By checking the operatingconditionat shut down, minimum diluting time is determinedautomatically. Interlocking circuits of auxiliary devices are equippedas a standard. For a power-failure within the minutes, the unit may start automatically after the power is recovered. The unit will shut down with alarm if the power failure lasts more than ten minutes.
DirectFired Absorption Chiller-Heater ol withlatest microprocess equipped or environment, CONTENTS In an application of inverter control of solution puffiF, saving energy has been realized in the whole range from partial loads to rated loads of cooling mode. Installation costs may be reduced at no control of cooling water temperature and further saving in energy consumptiong as operation is feasible as 15'C at the inlet of cooling water. Note 2 This graphic chart is applicabte to the model through Note 3 An area surroundedby the dotted lines is the area for available loads.
Refrigerant evaporates in an evaporator and cools down chilled water. The evaporated refrigerant is absorbed into the solution in the absorber. The solution absorbed the refrigerant become weak and sends to the high and low temperature generator respectively through the heat-excangers pumped up by the solution pump.
The weak solution turns to a concentrated strong solution after heating by the burner in the high temperature generator. The solution becomes medium strong solution in the low temperature generator heated by refrigerant steam generated in the high temperature generator.
The strong solution in the high and medium strong solution in the low temperature are mixed together and back to absorber through the both solution heat-exchangers, in which absorbs the refrigerant evaporated from the evaporator.
The generated refrigerant in the low temperature generator move to the condenser and condensed by the cooling water. Condensed refrigerant back to evaporator. The high temperature steam refrigerant generated in the high temperature generator is moved through valve and condensed in the evaporator and heating up hot water for heating. The refrigerant is down to and mixed up with medium weak solution in the absorber. Then pump up to the high temperaturegenerator by solution pump.
The medium weak solution generates steam refrigerant vapor in the high temperature generator. S llo. N Note 1 The standard chilled water temperatureis 12"c at the inlet and 7"C at the outlet, the cooling water temperature is 32"C at theinlet and Note 3 The capacity of burner fan may be changed on the combustion volume and the gas specification.
Note 6 Standarddeliveryis one piece shippingas the standard. Note 8 Dimensionin width may vary dependenton the gas specification. Please check the outline drawing in detail. Note 9 The wiring size is used for reference. Capacity Power Su0ply kVA mm' 10 5. Note 1 The standard chilled water temperature is 12"Cat the inlet and 7"C at the outlet, the cooling water temperature is 32'C at theinlet and The values shown herein is based on the supply specificationat 2OOmmAq and are at the supply on mmAq.
Note 1 The standard chilled water temperature is i2"c at the inlet and 7'C at the outlet, the cooling water temperature is C at theinlet and O 7. Evaporator shell. Evaporator water box and box cover. Refrigerant pumpand piping. Model RCDF ,! N 't NO21 NO28 NO32 't 't NO36 NO45 24BO NO50 NO60 ' NO70 When the temperature of cooling water is below 15'C, the temperature control of the cooling water is required.
Provide the comparison flanges by others. Install the drainage at the bottom of flue and chimney as required. For the chimney and flue, care must be exercised in designing and planning not to allow chimney in common use with other incinerator or engine generator or other devices.
In design and planning, sharp corners or flue area must be avoided. Cooling tower shall be located far from the outlet of chimney to avoid water pollution. For chemical cleaning, Install the stop valves for cleaning between the unit and each stop valve at the inlet or outlet. The followingtable showsa qualityguidelineof of the unit for a long time, ii is necessary For eificient operation Air conditioning Association JM.
Quality standard of feed water Values of standard 6. Valubs of standard 6. Note1 Whenpowersource is grounded, phase "s" mustbe gr6unded. TB2 1 - 2 - C Oo 3 - 4 - C1ostartsignall Note 2 interlock tower cooling I Fan, lE. Limitswitch,of motorvalve I Outsideemergencystopsignall Note2. Seismic sensor J'. Among input signals,utilize any input signal you need after removingany short circuit work finished in the panel in-house 3.
RS3'To connect with the white cable" Terminal no. RS4'To connect with the black cable. The shield must be groundedwith by either one of the earth terminals'. For out-put signals,select any signal necessary' Pteasespecify necessarysignals for selecting among the preset keys on the control panel of the unit. For connectionwiring with auxiliarydevices, rThe timer for startingthe dilution is included in the control panel of the unit. Anange wiring separatelybetweenV circuits and low voltage circuits.
This unit has various safety devices not only for safety operation but also for protecting the unit. With activation of the following devices, the unit will stop automatically with closing the shutoff valve of fuel and sounding buzzer simultaneously.
EBARA absorption chiller
Ebara provided seven direct-fired chillers for this commercial center of thousand square to meet summer cooling and winter heating demands. Using coking waste heat for heating and refrigeration, the company adopts double conditions absorption chiller unit. All these kinds of water have low temperature and large amount of residual heat. Heat pump technology are always used for recovering these residual heat source.
Absorption and centrifugal water chillers EBARA
Embed Size px x x x x Energy saving with minimized startup. Startup time of the system has been cr,it short with an op-timized flow rate of circulating solution responsive to thestartup operation quickly. This reduce fuel consumption. Reducing dilution time at the time of operatinginterruption. By checking the operating condit ion at shut down, minimumdilut ing t ime is determined automatical ly. Interlocking circuits of auxiliary devices areequipped as a standard.
RCD Ebara Absorption Chiller
This chiller achieves excellent energy efficiency over the entire operating range, from the rated load to prolonged partial load, with an inverter-controlled solution pump. This chiller optimizes the circulating amount of solution at the time of start-up to reduce the start-up time. The chiller judges the operation status at the time of stop to determine the optimum dilution time. The chiller can prevent extra dilution operation that reduces the energy-saving effect. Equipped with a start-stop circuit for the cooling tower fan as standard, including a thermos sensor, the chiller helps to reduce the cost of equipment. The chiller has a control panel that can digitally display data required for operation control, such as the chilled water temperature, cooling water temperature, solution temperature, and operating time, on an individual basis. USRT Features Shorter start-up time This chiller optimizes the circulating amount of solution at the time of start-up to reduce the start-up time.
ebara 16jh hot water type absorption refrigerating machine
Energysaving with minimizedstartup. Startup time of the system has been cr,it short with an optimized flow rate of circulating solution responsive to the startup operationquickly. This reduce fuel consumption. Operatingconditionis displayedon the panel digitally. Temperature in the high temperature generator. Dew point temp.