Trade Alerts are FREE updates on topics such as trending hot products, buying requests and supplier information - sent directly to your email inbox! Favorites Compare. Dongguan Feirui Electronics Co. Contact Details Video.
|Published (Last):||9 February 2012|
|PDF File Size:||9.83 Mb|
|ePub File Size:||4.98 Mb|
|Price:||Free* [*Free Regsitration Required]|
Quick Links. Download this manual. Table of Contents. Page 2 Sea Electronics Plc at the address above. Any reference to trademarked product names used within this publication is owned by their respective companies. Deep Sea Electronics Plc reserves the right to change the contents of this document without prior notice. Part No. Transfer of the load is automatic upon a mains supply failure. Always refer to your configuration source for the exact sequences and timers observed by any particular module in the field.
Viewing the instruments is NOT affected by panel lock. If panel lock is active the Panel lock indicator if configured illuminates. Viewing the instruments and event logs is NOT affected by panel lock.
In the event of an alarm the LCD will jump to the alarms page, and scroll through all active warnings and shutdowns. Alarm Warning Overspeed will be displayed. It is an immediate warning.
Alarm Warning High Current will be displayed. If this high current condition continues for an excess period of time, then the alarm is escalated to a shutdown condition. Alarm Shutdown High Engine Temperature will be displayed. Alarm Shutdown Low Volts will be displayed. Alarm Shutdown AC Undervolts Example The display will alternate Alarm Once this has occurred the module will start the Cooling timer and allow the engine to cool off-load before shutting down the engine.
The unit will respond to either a mains failure or an Mains on load active remote start. Modem Status The modem is reset by the series controller. The configuration cannot be viewed or changed until the PIN number is correctly entered. NOTE:- The controller maintains the current date and time so long as it is connected to a DC supply within the operating range.
Fixing is by 4 clips for easy assembly. Module can then be re-configured utilising the 5xxx series configuration software. See rear panel layout FIG 5. Do not connect this terminal to earth.
CAN port H. CAN port L. Connect to alternator L1 output. Generator L2 sensing input. Connect to alternator L2 output. If using single phase only do not connect this terminal. To check the start cycle operation take appropriate measures to prevent the engine from starting disable the operation of the fuel solenoid. After a visual inspection to ensure it is safe to proceed, connect the battery supply. Check the DC supply. Check the DC fuse. Absence of the icon beside an item means that adjustment of this parameter is only possible using the 5xxx series configuration software in conjunction with the P interface.
A change in fuel level translates directly to a change in the resistance of the sender. In the case of a parallel sided fuel tank, an accurate measure of the fuel level can easily be made, however as shown in the example below, this is not the case with non-parallel sided fuel tanks. CAN enabled engine controllers monitor the engines operating parameters such as engine speed, oil pressure, engine temperature among others in order to closely monitor and control the engine.
The operator is then able to remotely control the module, starting or stopping the generator, selecting operating modes, etc. It is possible to use third party software to monitor and control the module via this protocol. Please refer to Deep Sea Electronics Plc for details. This uses a master-slave technique to communicate. IP figures shown are approximate only.
Provides a degree of protection against contact with the enclosure equipment and against a limited amount of falling dirt. IP30 Provides a degree of protection against limited amounts of falling water and dirt.
This manual is also suitable for: Dse Print page 1 Print document 67 pages. Cancel Delete. Sign In OR. Don't have an account?
Sign up! Restore password. Upload from disk. Upload from URL.
Deep Sea Electronics Plc DSE5320 Operating Manual
Themodule also provides advanced engine monitoring and protection features. Upon detection of a mains utility failure the module automatically starts the generating set. Once the mains utility power has been restored the module instructs the generating set to stop. Both modules include RS or RS communication capabilities for linking to a PC, sending SMS messages and interfacing with new and existing building management systems. An additional push button allows the user to scroll through the LCD display.
Control Module DSE 5320 AMF RS485 / 8-36V 5320-02 Deep Sea Electronics
Quick Links. Download this manual. Table of Contents. Page 2 Sea Electronics Plc at the address above. Any reference to trademarked product names used within this publication is owned by their respective companies. Deep Sea Electronics Plc reserves the right to change the contents of this document without prior notice. Part No.